Combo Unit, Cold Weather, Red, LED Lighting, Sealed Lead Acid (SLA), Title 20 Products (2 items)
X Cold Weather
X LED Lighting
X Sealed Lead Acid (SLA)
X Title 20
Exit sign/emergency light combo units
Exit sign combo units are really a 2 for 1 solution and are the ideal solution where you need to install both an exit sign & an emergency light near each other. Exit combos allow you to maintain just one battery and unit while meeting two code requirements. There is a combo exit sign for almost every application and location.
Cold Weather emergency lights & exit signs
Batteries placed in cold environments can eventually fail or rupture. If your emergency lights or exit signs will be installed in temperatures below 20° F (-6° C), you may want to consider a cold weather option. Cold weather lights include a thermostatic battery heater which maintains the battery strength and lifespan in temperatures between -4° F (-20° C) and -40° F (-40° C) depending on the model you choose.
Red Letter Exit Signs
Red letters are required for New York City and Chicago approved exit signs.
Energy efficient LED exit signs & emergency lighting
Visibility, brightness and long life are very important factors that should be thought about when purchasing and exit sign. Light emitting diode or LED exit signs & emergency lights have proven to be successful in the reducing electricity consumption by up to 85%. LED exit signs can save money and power while still emitting considerable amounts of light.
Sealed lead acid (SLA) batteries
Sealed lead acid batteries are sometimes referred to as VRLA (valve regulated lead acid) and there are two primary types AGM and Gel. We offer both AGM and Gel batteries, each has its advantages over the other depending on the specific application. SLA batteries usually last between 3 to 5 years with typical usage. The optimum operating temperature for the lead-acid battery is 25°C (77°F). Elevated temperature reduces longevity. As a guideline, every 8°C (15°F) rise in temperature cuts the battery life in half.
What is Title 20?
Title 20 is part of the CEC's Appliance Efficiency Regulation and California Code of Regulations that requires
manufacturer certification of "self-contained” lighting control devices in California.
"Self-contained” lighting control devices are defined as discrete lighting control devices that can perform their
designed function without the requirement of being connected to additional devices.
Common devices that may fall under the category of "Self-contained” include:
- Self-contained Automatic Daylighting Controls
- Line powered Occupancy Sensors
- Line power Vacancy Sensors
Please call us at 763-292-5485 to speak with an expert, or email firstname.lastname@example.org to receive a quote.