Emergency Lights, Cold Weather, Sealed Lead Acid (SLA), Self-Testing, New York City Approved, Dual Circuit Products (2 items)
Emergency Lights | Buy UL listed emergency lighting
An emergency light is a lighting device with a battery backup that switches on automatically when a building experiences a power outage. Emergency lights are standard in commercial and high occupancy residential buildings, such as college dormitories. Most building codes require emergency lighting be installed in older buildings as well.
Cold Weather emergency lights & exit signs
Batteries placed in cold environments can eventually fail or rupture. If your emergency lights or exit signs will be installed in temperatures below 20° F (-6° C), you may want to consider a cold weather option. Cold weather lights include a thermostatic battery heater which maintains the battery strength and lifespan in temperatures between -4° F (-20° C) and -40° F (-40° C) depending on the model you choose.
Sealed lead acid (SLA) batteries
Sealed lead acid batteries are sometimes referred to as VRLA (valve regulated lead acid) and there are two primary types AGM and Gel. We offer both AGM and Gel batteries, each has its advantages over the other depending on the specific application. SLA batteries usually last between 3 to 5 years with typical usage. The optimum operating temperature for the lead-acid battery is 25°C (77°F). Elevated temperature reduces longevity. As a guideline, every 8°C (15°F) rise in temperature cuts the battery life in half.
Self-Diagnostics/Self-Testing exit signs & emergency lights
This feature may be added to many exit sign and emergency light fixtures, the SDT feature prolongs battery life, and reduced man hours required OSHA tests. Self testing diagnostic automatically executes a 15 minute test every 30 days and runs a 90 minutes test once per year. The major reasons batteries typically fail is because they remain dormant for long periods of time. With the SDT feature automatically simulates a full discharge and full recharge to keep the batteries in peak performance. If any problems arise during this testing process it will report them through the user interface. This benefit drastically reduces man hours required by OSHA to manually perform the tests.
New York City approved exit signs/emergency lights
New York City has very specific codes regarding emergency lighting and signage. In short New York City approved exit signs must be Red 8 inch tall letters with a 1 inch stroke (line thickness) as opposed to 6 inch tall with a 3/4 inch stroke in typical exit signs.
Dual circuit exit signs. These unit allows the fixture to have dual power feeds. The idea behind this is so that when on normal power, the fixture is fed from a switch leg and can be turned off by the occupant. The PTS relay coil is fed by unswitched normal power. The normal power from the switch leg is connected to the normally open contacts on the PTS relay.
Please call us at 763-292-5485 to speak with an expert, or email firstname.lastname@example.org to receive a quote.