Emergency Lights, Cold Weather, New York City Approved, Nickel-Cadmium (NiCd), Dual Circuit Products (2 items)
Emergency Lights | Buy UL listed emergency lighting
An emergency light is a lighting device with a battery backup that switches on automatically when a building experiences a power outage. Emergency lights are standard in commercial and high occupancy residential buildings, such as college dormitories. Most building codes require emergency lighting be installed in older buildings as well.
Cold Weather emergency lights & exit signs
Batteries placed in cold environments can eventually fail or rupture. If your emergency lights or exit signs will be installed in temperatures below 20° F (-6° C), you may want to consider a cold weather option. Cold weather lights include a thermostatic battery heater which maintains the battery strength and lifespan in temperatures between -4° F (-20° C) and -40° F (-40° C) depending on the model you choose.
New York City approved exit signs/emergency lights
New York City has very specific codes regarding emergency lighting and signage. In short New York City approved exit signs must be Red 8 inch tall letters with a 1 inch stroke (line thickness) as opposed to 6 inch tall with a 3/4 inch stroke in typical exit signs.
The nickel–cadmium battery is a type of rechargeable battery using nickel oxide hydroxide and metallic cadmium as electrodes. The abbreviation NiCd is derived from the chemical symbols of nickel and cadmium. NiCd batteries have a longer shelf life of around 10 years. The NiCd batteries sold on this site are High Temperature NiCds batteries with outstanding charge/discharge characteristics at both room temperature and high temperature up to 70°C (158°F).
Warning: Batteries, battery terminals, and related accessories can expose you to chemicals including Cadmium and Cadmium compounds, which are known to the State of California to cause cancer and birth defects or other reproductive harm. For more information go to https://www.p65warnings.ca.gov
Dual circuit exit signs. These unit allows the fixture to have dual power feeds. The idea behind this is so that when on normal power, the fixture is fed from a switch leg and can be turned off by the occupant. The PTS relay coil is fed by unswitched normal power. The normal power from the switch leg is connected to the normally open contacts on the PTS relay.
Please call us at 763-292-5485 to speak with an expert, or email firstname.lastname@example.org to receive a quote.