The main housing of these exit signs and emergency lights is painted white or made from a white thermoplastic.
The main housing of these exit signs and emergency lights is painted black or made from a black thermoplastic.
Red letters are required for New York City and Chicago approved exit signs.
Green letters are typically used in theater exit signs.
A damp location is an interior location normally subject to dampness or condensation, or an exterior location protected from weather and not subject to saturation with water. Damp locations include over bathtubs, indoor pools, covered porches, and like locations.
Remote capable exit signs or emergency lights allow the unit to add additional lighting with remote light heads without adding additional fixtures.
Wet Location emergency lights and exit signs are weatherproof and designed to be used in outdoor environments, as well as indoor locations that are exposed to water and moisture. Wet location emergency lights and exit signs are extremely durable and long-lasting.
Batteries placed in cold environments can eventually fail or rupture. If your emergency lights or exit signs will be installed in temperatures below 20° F (-6° C), you may want to consider a cold weather option. Cold weather lights include a thermostatic battery heater which maintains the battery strength and lifespan in temperatures between -4° F (-20° C) and -40° F (-40° C) depending on the model you choose.
This feature may be added to many exit sign and emergency light fixtures, the SDT feature prolongs battery life, and reduced man hours required OSHA tests. Self testing diagnostic automatically executes a 15 minute test every 30 days and runs a 90 minutes test once per year. The major reasons batteries typically fail is because they remain dormant for long periods of time. With the SDT feature automatically simulates a full discharge and full recharge to keep the batteries in peak performance. If any problems arise during this testing process it will report them through the user interface. This benefit drastically reduces man hours required by OSHA to manually perform the tests.
Visibility, brightness and long life are very important factors that should be thought about when purchasing and exit sign. Light emitting diode or LED exit signs & emergency lights have proven to be successful in the reducing electricity consumption by up to 85%. LED exit signs can save money and power while still emitting considerable amounts of light.
Exit sign combo units are really a 2 for 1 solution and are the ideal solution where you need to install both an exit sign & an emergency light near each other. Exit combos allow you to maintain just one battery and unit while meeting two code requirements. There is a combo exit sign for almost every application and location.
Products with internal heater option allow the units and batteries to operate properly at temperatures down to -50°C.
An emergency light with battery backup capability switches to emergency operation in the event of a power loss to illuminate escape routes and safety equipment.
NEMA rated enclosures are intended for indoor or outdoor use primarily to provide a degree of protection against the entry of water during prolonged submersion at a limited depth. NEMA 12 enclosures are designed to prevent the ingress of dust, water, and oil.
Hazardous location exit signs and emergency lights are designed to operate in hostile environments that would damage ordinary signs and lights. Constructed from corrosion resistant materials, some units offer sealed enclosures that can be used in outdoor environments or areas subject to water spray, moisture and extreme temperature conditions.
Outdoor lighting is lighting used to illuminate the areas, where there are no roofs, i.e., outdoor areas. Outdoor lights are able to be in the elements of including rain and cold weather.
These products can be hung from the ceiling. Many exit signs come with the ceiling mounting canopy included.
Exit signs & emergency lights that are surface mountable are typically one sided and have a back plate that can be connected directly to a wall or flat surface.
Architectural lighting is designed to be a highly functional style of lighting in spaces where light fixtures are needed to serve a fundamental purpose, such as providing focused downlight or accenting certain areas of a room. Often thought of as a practical type of lighting, these fixtures are not usually given credit for their decorative character and ability to add undeniable style to a lighting project.
Commercial lighting is lighting used for commercial spaces such as offices, stores, institutions, hospitals and government buildings, essentially those spaces that are not residential, industrial or for manufacturing.
Industrial modern blends the urban edge of utilitarian design with the warmth of aged woods and worn textures. Lighting utilize aged iron and metals with rich patinas, accented by weathered woods and soft neutral surfaces.
Title 20 is part of the CEC's Appliance Efficiency Regulation and California Code of Regulations that requires
manufacturer certification of "self-contained” lighting control devices in California.
"Self-contained” lighting control devices are defined as discrete lighting control devices that can perform their
designed function without the requirement of being connected to additional devices.
Common devices that may fall under the category of "Self-contained” include:
- Self-contained Automatic Daylighting Controls
- Line powered Occupancy Sensors
- Line power Vacancy Sensors
Lithium Iron Phosphate (LFP)
The lithium iron phosphate battery or LFP battery, is a type of lithium-ion battery using lithium iron phosphate as the cathode material, and a graphitic carbon electrode with a metallic backing as the anode. The energy density of LiFePO? is lower than that of lithium cobalt oxide, and also has a lower operating voltage. The charge-discharge profiles of LFP cells are typically very flat. The main drawback of LiFePO? is its low electrical conductivity. Therefore, all the LiFePO? cathodes under consideration are actually LiFePO?/C. Because of low cost, low toxicity, well-defined performance, long-term stability, etc. LiFePO? is finding a number of roles in vehicle use, utility scale stationary applications, and backup power. LFP batteries are cobalt-free.