An emergency light is a lighting device with a battery backup that switches on automatically when a building experiences a power outage. Emergency lights are standard in commercial and high occupancy residential buildings, such as college dormitories. Most building codes require emergency lighting be installed in older buildings as well.
The main housing of these exit signs and emergency lights is painted white or made from a white thermoplastic.
The main housing of these exit signs and emergency lights is painted black or made from a black thermoplastic.
Federally approved high temperature 4.8 Volt exit sign and emergency lighting NiCd batteries. A 4.8 Volt NiCd has four AA, AAA, C, Sub-C, D or F cells in a battery pack that can come in a variety of configurations. Most common are cube, row and stick configurations.
The nickel–cadmium battery is a type of rechargeable battery using nickel oxide hydroxide and metallic cadmium as electrodes. The abbreviation NiCd is derived from the chemical symbols of nickel and cadmium. NiCd batteries have a longer shelf life of around 10 years. The NiCd batteries sold on this site are High Temperature NiCds batteries with outstanding charge/discharge characteristics at both room temperature and high temperature up to 70°C (158°F).
Warning: Batteries, battery terminals, and related accessories can expose you to chemicals including Cadmium and Cadmium compounds, which are known to the State of California to cause cancer and birth defects or other reproductive harm. For more information go to https://www.p65warnings.ca.gov
A damp location is an interior location normally subject to dampness or condensation, or an exterior location protected from weather and not subject to saturation with water. Damp locations include over bathtubs, indoor pools, covered porches, and like locations.
Brushed die-cast aluminum housings provide a modern appearance with ultimate functionality.
Wet Location emergency lights and exit signs are weatherproof and designed to be used in outdoor environments, as well as indoor locations that are exposed to water and moisture. Wet location emergency lights and exit signs are extremely durable and long-lasting.
Batteries placed in cold environments can eventually fail or rupture. If your emergency lights or exit signs will be installed in temperatures below 20° F (-6° C), you may want to consider a cold weather option. Cold weather lights include a thermostatic battery heater which maintains the battery strength and lifespan in temperatures between -4° F (-20° C) and -40° F (-40° C) depending on the model you choose.
This feature may be added to many exit sign and emergency light fixtures, the SDT feature prolongs battery life, and reduced man hours required OSHA tests. Self testing diagnostic automatically executes a 15 minute test every 30 days and runs a 90 minutes test once per year. The major reasons batteries typically fail is because they remain dormant for long periods of time. With the SDT feature automatically simulates a full discharge and full recharge to keep the batteries in peak performance. If any problems arise during this testing process it will report them through the user interface. This benefit drastically reduces man hours required by OSHA to manually perform the tests.
Products with internal heater option allow the units and batteries to operate properly at temperatures down to -50°C.
An emergency light with battery backup capability switches to emergency operation in the event of a power loss to illuminate escape routes and safety equipment.
A photocell senses current lighting condition and when lighting conditions are dark it turns on your emergency lights and back off with lighting is bright enough to see. Photo sensor controls help save energy and money when paired with outdoor light fixtures in various industrial, commercial, and residential applications.
Outdoor lighting is lighting used to illuminate the areas, where there are no roofs, i.e., outdoor areas. Outdoor lights are able to be in the elements of including rain and cold weather.
Exit signs & emergency lights that are surface mountable are typically one sided and have a back plate that can be connected directly to a wall or flat surface.
Title 20 is part of the Appliance Efficiency Regulation and California Code of Regulations that requires
manufacturer certification of "self-contained” lighting control devices in California.
"Self-contained” lighting control devices are defined as discrete lighting control devices that can perform their
designed function without the requirement of being connected to additional devices.
Common devices that may fall under the category of "Self-contained” include:
- Self-contained Automatic Daylighting Controls
- Line powered Occupancy Sensors
- Line power Vacancy Sensors