An emergency light is a lighting device with a battery backup that switches on automatically when a building experiences a power outage. Emergency lights are standard in commercial and high occupancy residential buildings, such as college dormitories. Most building codes require emergency lighting be installed in older buildings as well.
The main housing of these exit signs and emergency lights is painted white or made from a white thermoplastic.
The main housing of these exit signs and emergency lights is painted black or made from a black thermoplastic.
Sealed Lead Acid (SLA)
Sealed lead acid batteries are sometimes referred to as VRLA (valve regulated lead acid) and there are two primary types AGM and Gel. We offer both AGM and Gel batteries, each has its advantages over the other depending on the specific application. SLA batteries usually last between 3 to 5 years with typical usage. The optimum operating temperature for the lead-acid battery is 25°C (77°F). Elevated temperature reduces longevity. As a guideline, every 8°C (15°F) rise in temperature cuts the battery life in half.
A damp location is an interior location normally subject to dampness or condensation, or an exterior location protected from weather and not subject to saturation with water. Damp locations include over bathtubs, indoor pools, covered porches, and like locations.
Batteries placed in cold environments can eventually fail or rupture. If your emergency lights or exit signs will be installed in temperatures below 20° F (-6° C), you may want to consider a cold weather option. Cold weather lights include a thermostatic battery heater which maintains the battery strength and lifespan in temperatures between -4° F (-20° C) and -40° F (-40° C) depending on the model you choose.
Assembled In America
Products displaying an 'Assembled in the USA' label will contain a percentage of imported components but will be physically assembled in America. The FTC states that Assembled in America products must have undergone a significant transformation on American soil.
This feature may be added to many exit sign and emergency light fixtures, the SDT feature prolongs battery life, and reduced man hours required OSHA tests. Self testing diagnostic automatically executes a 15 minute test every 30 days and runs a 90 minutes test once per year. The major reasons batteries typically fail is because they remain dormant for long periods of time. With the SDT feature automatically simulates a full discharge and full recharge to keep the batteries in peak performance. If any problems arise during this testing process it will report them through the user interface. This benefit drastically reduces man hours required by OSHA to manually perform the tests.
Products with internal heater option allow the units and batteries to operate properly at temperatures down to -50°C.
An emergency light with battery backup capability switches to emergency operation in the event of a power loss to illuminate escape routes and safety equipment.
Title 20 is part of the Appliance Efficiency Regulation and California Code of Regulations that requires
manufacturer certification of "self-contained” lighting control devices in California.
"Self-contained” lighting control devices are defined as discrete lighting control devices that can perform their
designed function without the requirement of being connected to additional devices.
Common devices that may fall under the category of "Self-contained” include:
- Self-contained Automatic Daylighting Controls
- Line powered Occupancy Sensors
- Line power Vacancy Sensors